福禄克Fluke OptiFiber® Pro OTDR系列
福禄克Fluke SimpliFiber® Pro光功率计和光纤测试仪
福禄克Fluke Fiber QuickMap™多模光纤距离和故障定位仪
福禄克Fluke Fiber OneShot™ PRO光纤测试仪
福禄克Fluke VisiFault™ Visual Fault Locator电缆连通性测试仪
福禄克Fluke MultiFiber™ Pro光功率计及光纤测试工具包
福禄克Fluke FI-7000 FiberInspector™ Pro光纤显微摄像机
134 1039 1245
If you have access to YouTube, you can click here to watch a video of this new feature in action.
In data centers where the shield is typically grounded at both ends, ANY wire map tester will report the shield as connected, even if it is not. That's because the shield test is a simple DC Resistance measurement. If the shield is open, it will find the remote unit using the building ground (earth).
The DSX CableAnalyzer offers a unique solution to this problem. It ties the four pairs together and then sends a differential signal down the cable treating the shield as the second conductor. This allows the DSX CableAnalyzer to view the shield in the time domain. So even if the patch panels are grounded, it will report the shield open, if indeed it is open you would see:
And since it is using time domain techniques, the distance to the open is given. In this example, we can see the patch panel at the near end is the issue.
The scenario above occurs when the technician grounds the connector on the non conductive side of the cable shield. The result is degraded Alien Crosstalk performance. Since users are told that shielded cabling systems do not need to be tested for Alien Crosstalk, one wonders how wide spread this issue is and whether users are getting the performance they paid for.
If you only use the drain wire to connect the shield and that drain wire is greater than approx. 2 inches (5 cm), the DSX CableAnalyzer may report the shield as open. This is by design. Such a termination acts as an open circuit at the frequencies we are talking about here.
Copyright© 1998-2023深圳市连讯达电子技术开发有限公司 All Rights Reserved .
备案号： 粤ICP备18089363号 网站地图
免责声明：福禄克、FLUKE、FLUKE NETWORKS、 NETALLY等品牌资料及图片摘自网络，连讯公司不拥有以上品牌商标及相关产品著作权。